Optimization of Solar Energy System for the Electric Vehicle at University Campus in Dhaka, Bangladesh

The incorporation of renewable energy and the transportation system can be significantly beneficial for the economy and environment of Bangladesh. The main energy source for vehicles in Bangladesh are the country’s natural gas and fuel. However, due to the rapid depletion of the gas reserve, soaring gas prices and global warming, alongside the environmental pollution caused by burning fuel, this raises concerns about these energy sources. Renewable energy offers a plausible solution to these problems. This paper’s objective is to focus on the maximum usages of a solar photovoltaic (PV) system in electrical vehicles and to minimize the environmental impact in terms of CO2 emission. This system may be partially used to power up the electric vehicle with a charging facility and contribute excess power to the national grid. The modeling, with its optimal analysis of the green transportation system, is simulated using the Hybrid Optimization of Multiple Energy Renewables (HOMER) software. The energy produced by the PV system can provide up to 13,792 kWh/year. Approximately 21% of the total production can be used in the charging station for charging the electrical vehicles and the rest of the energy can contribute to the national grid. Moreover, using the proposed concept of green transport will ultimately reduce greenhouse gas emissions by 52,944 kg/year.


Introduction
Transportation plays a vital role in every society. It facilitates the cultivation of a lifestyle and enables the delivery of goods and services that promote the development of society. Within global efforts to increase the sustainability of development patterns, certain strategies for increasing transportation's sustainability have been articulated. These include vehicle technology improvements and clean fuels. Thus, the transportation system has a significant importance for the balanced development of economic and social systems of a country. One of the major problems of the global transport system is a high dependence on fossil fuels including oil and gas. One-third of the total final energy consumption is a result of the transport sector, including passenger and freight journeys, based on fossil fuels [1].
In particular, oil is the main energy provider in the transport energy. According to a report, 94% of the total energy demand for transport is provided by oil, 3% by natural gas and other fuels, 2% by The paper is structured in this manner: Section 2, provides a description of a solar photovoltaic system installed in Dhaka. Section 3 introduces the concept of electric buses with a connection and services for the Campus. In Section 4, the renewable energy sources, the load profiles, and the details of the system design using HOMER are presented. Section 5 provides the proposed green transportation model and discussion of the simulation results, while the conclusions are presented in Section 6.

Existing Solar PV System Installed in Dhaka University Campus
The Institute of Energy in the University of Dhaka (DU) is located near Curzon hall. It has a huge area covered with buildings, but one side of the adjacent area is equipped with a 9.9 kW solar Photovoltaic System with a capacity of 10 kW, active since January 2014. The electric characteristics of PV modules are labeled under the term of STC (Standard Test Conditions), which are solar irradiation of 1000 W/m 2 , solar spectrum AM 1.5 and temperature of 25 • C. Figure 1 shows the PV systems located in the University.
Energies 2018, 11, x FOR PEER REVIEW 3 of 10 services for the Campus. In Section 4, the renewable energy sources, the load profiles, and the details of the system design using HOMER are presented. Section 5 provides the proposed green transportation model and discussion of the simulation results, while the conclusions are presented in Section 6.

Existing Solar PV System Installed in Dhaka University Campus
The Institute of Energy in the University of Dhaka (DU) is located near Curzon hall. It has a huge area covered with buildings, but one side of the adjacent area is equipped with a 9.9 kW solar Photovoltaic System with a capacity of 10 kW, active since January 2014. The electric characteristics of PV modules are labeled under the term of STC (Standard Test Conditions), which are solar irradiation of 1000 W/m 2 , solar spectrum AM 1.5 and temperature of 25 °C. Figure 1 shows the PV systems located in the University. The monthly solar radiation data for the Dhaka university campus area (latitude of 23°43′ North and longitude of 90°25′ East) are collected from HOMER via a NASA satellite [19]. In Figure 2, the Global Horizontal Radiation (GHR) curve for twelve months is presented. The scaled annual average radiation for Bangladesh is equal to 4.59 kWh/m 2 /day.  The monthly solar radiation data for the Dhaka university campus area (latitude of 23 • 43 North and longitude of 90 • 25 East) are collected from HOMER via a NASA satellite [19]. In Figure 2, the Global Horizontal Radiation (GHR) curve for twelve months is presented. The scaled annual average radiation for Bangladesh is equal to 4.59 kWh/m 2 /day. services for the Campus. In Section 4, the renewable energy sources, the load profiles, and the details of the system design using HOMER are presented. Section 5 provides the proposed green transportation model and discussion of the simulation results, while the conclusions are presented in Section 6.

Existing Solar PV System Installed in Dhaka University Campus
The Institute of Energy in the University of Dhaka (DU) is located near Curzon hall. It has a huge area covered with buildings, but one side of the adjacent area is equipped with a 9.9 kW solar Photovoltaic System with a capacity of 10 kW, active since January 2014. The electric characteristics of PV modules are labeled under the term of STC (Standard Test Conditions), which are solar irradiation of 1000 W/m 2 , solar spectrum AM 1.5 and temperature of 25 °C. Figure 1 shows the PV systems located in the University. The monthly solar radiation data for the Dhaka university campus area (latitude of 23°43′ North and longitude of 90°25′ East) are collected from HOMER via a NASA satellite [19]. In Figure 2, the Global Horizontal Radiation (GHR) curve for twelve months is presented. The scaled annual average radiation for Bangladesh is equal to 4.59 kWh/m 2 /day.

Proposed Electric Buses for the University
According to the Bangladesh Road Transport Authority (BRTA), more than fifty thousand Electric Vehicles (EVs) are available in each of Bangladesh's major cities. The EVs include battery-operated Auto rickshaw, electrically motorized rickshaw, electric two-wheelers, and electric bicycles [17]. While no electrical buses are currently available in Bangladesh, a battery operated electrical bus for the students of the Dhaka University is proposed. A charging station for this electric bus will be designed with a 9.9 kW solar Photovoltaic System near the University, described in the previous section. This bus will be useful for pick-up and drop-off for students at different locations throughout Dhaka city. Due to the unavailability, this kind of bus can either be imported, constructed, or fabricated from the local market. In this situation, the initial cost could be higher in the long run; however, it is highly beneficial for the country.
A bus with 14 seats is described in Table 1. It has a driving capacity of 100 km. Battery capacity has a range of 8.64 kWh, while its maximum speed is 40 km/h and the energy consumption is 0.086 kWh/km [20]. In this paper, two electrical buses have been considered and all characteristics are indicated in Table 1. According to the Bangladesh Road Transport Authority (BRTA), more than fifty thousand Electric Vehicles (EVs) are available in each of Bangladesh's major cities. The EVs include batteryoperated Auto rickshaw, electrically motorized rickshaw, electric two-wheelers, and electric bicycles [17]. While no electrical buses are currently available in Bangladesh, a battery operated electrical bus for the students of the Dhaka University is proposed. A charging station for this electric bus will be designed with a 9.9 kW solar Photovoltaic System near the University, described in the previous section. This bus will be useful for pick-up and drop-off for students at different locations throughout Dhaka city. Due to the unavailability, this kind of bus can either be imported, constructed, or fabricated from the local market. In this situation, the initial cost could be higher in the long run; however, it is highly beneficial for the country.
A bus with 14 seats is described in Table 1. It has a driving capacity of 100 km. Battery capacity has a range of 8.64 kWh, while its maximum speed is 40 km/h and the energy consumption is 0.086 kWh/km [20]. In this paper, two electrical buses have been considered and all characteristics are indicated in Table 1. Obviously, the energy that must be provided to the vehicles depends on the difference between the initial and final States of Charge of the battery (ΔSOC). To calculate the energy required (Erich) for each type of Electric Bus, it is possible to use the expression in (1): Particular attention is drawn to the time needed for recharging consumed energy ( ), which is equal to: where Pcharge is the charging power of the battery. As mentioned earlier, the electric bus as a form of green transportation is proposed for use by students of Dhaka University. It will be used for their pick-up and drop-off at the University. Once it is charged up from the CS, which is a 9.9 kW PV system, it would go on the drop-off and then return to the charging station.

LQY140A LQY140AN (Gear Box)
Qty/20 GP Obviously, the energy that must be provided to the vehicles depends on the difference between the initial and final States of Charge of the battery (∆SOC). To calculate the energy required (E rich ) for each type of Electric Bus, it is possible to use the expression in (1): Particular attention is drawn to the time needed for recharging consumed energy (t recharge ), which is equal to: where P charge is the charging power of the battery. As mentioned earlier, the electric bus as a form of green transportation is proposed for use by students of Dhaka University. It will be used for their pick-up and drop-off at the University. Once it is charged up from the CS, which is a 9.9 kW PV system, it would go on the drop-off and then return to the charging station.
In this paper, two routes have been selected. The first route is from Dhaka University campus to Uttara and is approximately 21.4 km (Figure 3a). The second route is from Dhaka University campus to Jatra Bari. The bus could either move through the Jatrabari Gulsan flyover, which is 6.9 km, or through Kazi Nazrul Islam Avenue, which is 21.3 km from the campus (Figure 3b).
Energies 2018, 11, x FOR PEER REVIEW 5 of 10 In this paper, two routes have been selected. The first route is from Dhaka University campus to Uttara and is approximately 21.4 km (Figure 3a). The second route is from Dhaka University campus to Jatra Bari. The bus could either move through the Jatrabari Gulsan flyover, which is 6.9 km, or through Kazi Nazrul Islam Avenue, which is 21.3 km from the campus (Figure 3b). It has been considered that the bus must run four trips per day and each trip must cover 42.7 km, so the total number of monthly trips will be 100. Buses cover then 51,240 km/year and need to charge their battery 510 times per year. Therefore, annual energy consumption per year will be 4406.64 kWh.

Renewable Energy Sources, Load Profile, and System Design Using HOMER
The HOMER (Hybrid Optimization of Multiple Energy Resources) beta 2.68 version is a popular simulation tool used for designing micro-grids that combine traditionally generated and renewable power, storage, and load management with minimum per unit energy production cost. It is reliable for micro-grid design optimization and feasibility for variations in technology costs, electric load, and energy resource availability [18].

Load Profile Based on Collected Data
The monthly load profile is considered based on the demand of the campus. The load profile varies between November to January when it is very low because the university is closed at that time. From February to October, the load consumption becomes higher and the average kWh per day required is 50.3 with a peak demand of 7.64 kW where the load factor is 0.274. In Figure 4 the profile, a scaled data monthly averages of load, is provided [18].  It has been considered that the bus must run four trips per day and each trip must cover 42.7 km, so the total number of monthly trips will be 100. Buses cover then 51,240 km/year and need to charge their battery 510 times per year. Therefore, annual energy consumption per year will be 4406.64 kWh.

Renewable Energy Sources, Load Profile, and System Design Using HOMER
The HOMER (Hybrid Optimization of Multiple Energy Resources) beta 2.68 version is a popular simulation tool used for designing micro-grids that combine traditionally generated and renewable power, storage, and load management with minimum per unit energy production cost. It is reliable for micro-grid design optimization and feasibility for variations in technology costs, electric load, and energy resource availability [18].

Load Profile Based on Collected Data
The monthly load profile is considered based on the demand of the campus. The load profile varies between November to January when it is very low because the university is closed at that time. From February to October, the load consumption becomes higher and the average kWh per day required is 50.3 with a peak demand of 7.64 kW where the load factor is 0.274. In Figure 4 the profile, a scaled data monthly averages of load, is provided [18]. In this paper, two routes have been selected. The first route is from Dhaka University campus to Uttara and is approximately 21.4 km (Figure 3a). The second route is from Dhaka University campus to Jatra Bari. The bus could either move through the Jatrabari Gulsan flyover, which is 6.9 km, or through Kazi Nazrul Islam Avenue, which is 21.3 km from the campus (Figure 3b). It has been considered that the bus must run four trips per day and each trip must cover 42.7 km, so the total number of monthly trips will be 100. Buses cover then 51,240 km/year and need to charge their battery 510 times per year. Therefore, annual energy consumption per year will be 4406.64 kWh.

Renewable Energy Sources, Load Profile, and System Design Using HOMER
The HOMER (Hybrid Optimization of Multiple Energy Resources) beta 2.68 version is a popular simulation tool used for designing micro-grids that combine traditionally generated and renewable power, storage, and load management with minimum per unit energy production cost. It is reliable for micro-grid design optimization and feasibility for variations in technology costs, electric load, and energy resource availability [18].

Load Profile Based on Collected Data
The monthly load profile is considered based on the demand of the campus. The load profile varies between November to January when it is very low because the university is closed at that time. From February to October, the load consumption becomes higher and the average kWh per day required is 50.3 with a peak demand of 7.64 kW where the load factor is 0.274. In Figure 4 the profile, a scaled data monthly averages of load, is provided [18].  In HOMER according to the load consumption, an off peak time from 7 p.m. to 6 a.m. is assumed when the load consumption is low, while the peak time starts from 6 a.m. and ends at 6 p.m. The daily load variation is shown in Figure 5. In HOMER according to the load consumption, an off peak time from 7 p.m. to 6 a.m. is assumed when the load consumption is low, while the peak time starts from 6 a.m. and ends at 6 p.m. The daily load variation is shown in Figure 5.

Size Consideration of Solar Photovoltaic Array
To determine the PV size, different panel combinations are inserted in the HOMER software along with other parameters to optimize the system's performance. 20 years lifetime for the PV has been considered and no tracking system has been employed [21,22]. The installation cost of PV arrays is $0.0/WP because already 9.9 kW PV systems have been installed at the Dhaka University premises. Moreover, to charge up the full battery of one bus, 2.2 kW is required daily in view of use during peak hours 11 a.m. to 3 p.m. Therefore, two buses would require 4 kW per day, which can easily be supplied from the installed PV system. Installation, replacement, and operating and maintenance (O&M) costs for 1 kW PV are taken as $0, $1050 and $2/year respectively.

Battery Size and Converter
Electricity has been supplied from a battery to run the bus. This paper considered a battery that has nominal voltage of 6 V, and a nominal capacity of 120 Ah (8.64 kWh per day). The battery will be charged up from the charging station. The lifetime of the battery is assumed to be 5 years. The installation, replacement, and operating & maintenance costs of one battery are taken as $200, $800, and $1.2/year, respectively. A fully-charged battery requires 4 h of charging.
The converter is a vital part of the renewable power generating system. The converter is used to convert the power from AC to DC or vice versa. For a 1 kW converter, the installation and replacement costs are considered to be $220 and $250, respectively. Converter sizes considered in the simulations are 1 kW up to 11 kW as the installed PV capacity is 10 kW. Inverter lifetime and efficiency are taken as 15 years and 90%. Rectifier capacity relative to the inverter is considered as 100% and efficiency is considered as 85%. O&M costs of a 1 kW converter are $20 per year.

Grid Connection to Microgrid System
A grid integrated distributed generation has recently become popular. In this paper, it is considered that connecting the whole microgrid system, where the remaining power supplies the national grid of Bangladesh to further grow economic development with a profitable sell back price, will occur. Maximum grid demand is kept at zero, which means that the microgrid system cannot draw power from the grid other than sales of maximum 20 kW per year to the grid. Grid interconnection charge and standby charges are estimated at $0 (considering $270/kW) [23,24] and $100 per year. Scheduled rates of electricity in Bangladesh are given below in Table 2.

Size Consideration of Solar Photovoltaic Array
To determine the PV size, different panel combinations are inserted in the HOMER software along with other parameters to optimize the system's performance. 20 years lifetime for the PV has been considered and no tracking system has been employed [21,22]. The installation cost of PV arrays is $0.0/WP because already 9.9 kW PV systems have been installed at the Dhaka University premises. Moreover, to charge up the full battery of one bus, 2.2 kW is required daily in view of use during peak hours 11 a.m. to 3 p.m. Therefore, two buses would require 4 kW per day, which can easily be supplied from the installed PV system. Installation, replacement, and operating and maintenance (O&M) costs for 1 kW PV are taken as $0, $1050 and $2/year respectively.

Battery Size and Converter
Electricity has been supplied from a battery to run the bus. This paper considered a battery that has nominal voltage of 6 V, and a nominal capacity of 120 Ah (8.64 kWh per day). The battery will be charged up from the charging station. The lifetime of the battery is assumed to be 5 years. The installation, replacement, and operating & maintenance costs of one battery are taken as $200, $800, and $1.2/year, respectively. A fully-charged battery requires 4 h of charging.
The converter is a vital part of the renewable power generating system. The converter is used to convert the power from AC to DC or vice versa. For a 1 kW converter, the installation and replacement costs are considered to be $220 and $250, respectively. Converter sizes considered in the simulations are 1 kW up to 11 kW as the installed PV capacity is 10 kW. Inverter lifetime and efficiency are taken as 15 years and 90%. Rectifier capacity relative to the inverter is considered as 100% and efficiency is considered as 85%. O&M costs of a 1 kW converter are $20 per year.

Grid Connection to Microgrid System
A grid integrated distributed generation has recently become popular. In this paper, it is considered that connecting the whole microgrid system, where the remaining power supplies the national grid of Bangladesh to further grow economic development with a profitable sell back price, will occur. Maximum grid demand is kept at zero, which means that the microgrid system cannot draw power from the grid other than sales of maximum 20 kW per year to the grid. Grid interconnection charge and standby charges are estimated at $0 (considering $270/kW) [23,24] and $100 per year. Scheduled rates of electricity in Bangladesh are given below in Table 2.

Green Transportation Model, Simulation Results, and Discussion
The microgrid system for green transportation in HOMER software chooses the option called "System is connected to grid". All the components of producing renewable energy are stored in the HOMER library. In Figure 6, the designed system is shown with a proper arrangement to generate clean energy. Here the batteries act as a load that is fed by PV arrays. After charging the full battery, the remaining PV output is added to the grid. The converter is used here to convert the DC output into the AC output.

Green Transportation Model, Simulation Results, and Discussion
The microgrid system for green transportation in HOMER software chooses the option called "System is connected to grid". All the components of producing renewable energy are stored in the HOMER library. In Figure 6, the designed system is shown with a proper arrangement to generate clean energy. Here the batteries act as a load that is fed by PV arrays. After charging the full battery, the remaining PV output is added to the grid. The converter is used here to convert the DC output into the AC output. Before the simulations were initiated, all the costs of the components and monthly data of resources were mentioned in the HOMER simulation tool to find out the optimal size of the system. After simulations were done, HOMER finally showed the exact size & combination to build up the system with an initial capital of $2750, a minimum production cost of energy of $0.012 (BDT 0.936; 1 USD = BDT 78), and a renewable fraction of 1.00, which means the system is a 100% noiseless and decontaminated power generating project. HOMER showed the final optimum result for a 9 kW PV with a 11 kW converter. Figure 7 shows the monthly average electricity production by the PV array. The yellow portion resembles the monthly average electricity production by the PV array. In our proposed system the vehicles can be completely charged using the energy produced by RET, hence no additional energy is required from the grid, as a result the gray portion is not highlighted.  Before the simulations were initiated, all the costs of the components and monthly data of resources were mentioned in the HOMER simulation tool to find out the optimal size of the system. After simulations were done, HOMER finally showed the exact size & combination to build up the system with an initial capital of $2750, a minimum production cost of energy of $0.012 (BDT 0.936; 1 USD = BDT 78), and a renewable fraction of 1.00, which means the system is a 100% noiseless and decontaminated power generating project. HOMER showed the final optimum result for a 9 kW PV with a 11 kW converter. Figure 7 shows the monthly average electricity production by the PV array. The yellow portion resembles the monthly average electricity production by the PV array. In our proposed system the vehicles can be completely charged using the energy produced by RET, hence no additional energy is required from the grid, as a result the gray portion is not highlighted.

Green Transportation Model, Simulation Results, and Discussion
The microgrid system for green transportation in HOMER software chooses the option called "System is connected to grid". All the components of producing renewable energy are stored in the HOMER library. In Figure 6, the designed system is shown with a proper arrangement to generate clean energy. Here the batteries act as a load that is fed by PV arrays. After charging the full battery, the remaining PV output is added to the grid. The converter is used here to convert the DC output into the AC output. Before the simulations were initiated, all the costs of the components and monthly data of resources were mentioned in the HOMER simulation tool to find out the optimal size of the system. After simulations were done, HOMER finally showed the exact size & combination to build up the system with an initial capital of $2750, a minimum production cost of energy of $0.012 (BDT 0.936; 1 USD = BDT 78), and a renewable fraction of 1.00, which means the system is a 100% noiseless and decontaminated power generating project. HOMER showed the final optimum result for a 9 kW PV with a 11 kW converter. Figure 7 shows the monthly average electricity production by the PV array. The yellow portion resembles the monthly average electricity production by the PV array. In our proposed system the vehicles can be completely charged using the energy produced by RET, hence no additional energy is required from the grid, as a result the gray portion is not highlighted.  From the optimum result of the simulation, total annual generation from the PV array is 13,792 kWh and the annual demand for the charging station is 2861 kWh. The extra energy can be retailed to the grid, which is 9837 kWh/year. Total kilometer cover per trip is 42.7 km. HOMER depicts only~1 ($0.012) taka per unit cost for harnessing energy from the hybrid microgrid system deployed in the Dhaka University campus with a feasible net present cost (NPC) of $676 (equivalent to BDT 54080). The variability of services can be developed and distributed in different ways because the same services could be offered with different frequencies during the days of the week or month. However, from this analysis, the system provides 23% of its energy generated for charging up the electric vehicles while the remaining 77% of the energy is sold back to the grid annually. It is remarkable for a country like Bangladesh to be able to provide extra energy to meet the daily demand.
It is also important to consider the environmental impact in terms of CO 2 emission by the consumption of such conventional vehicles. The total emissions of CO 2 from a conventional vehicle can be calculated as [25]: where CO 2,CV is total emissions of CO 2 from the conventional vehicle for each kilometer travelled; FC is fuel consumption expressed in g/km; CO 2,g is the amount of CO 2 produced from the combustion of a gram of gasoline. The complete combustion of 1 L of gasoline produces 2.4 kg of CO 2 . Assuming a density of 700 kg/m 3 , 1 g of gasoline produces 3.42 g of CO 2 [25]. Finally, CF w is a correction factor that takes into account the production and distribution of gasoline. Sullivan et al. (2004) suggests a correction factor of 1.162 for gasoline cars [24]. In conventional vehicles, which have on average 11.102 L/42.7 km of fuel consumption, the CO 2 emission can be calculated around 1033.25 g/km/trip. In our case, per year the vehicle needs to cover around 51,240 km, which in turns gives per year CO 2 emission of approximately 52,943.75 kg/year, this value has been calculated considering the route distance of 42.7 km per trip, which is currently being travelled using conventional gasoline engine busses whose approximate fuel consumption is around 11.102 L. We have considered 14 seated buses for our calculation. However, this value may vary depending on different road and driving conditions. Figure 8 shows yearly CO 2 emissions for the oil-based transport system. Hence, we can clearly see that our proposed model can also save the environment by reducing CO 2 emissions. From the optimum result of the simulation, total annual generation from the PV array is 13,792 kWh and the annual demand for the charging station is 2861 kWh. The extra energy can be retailed to the grid, which is 9837 kWh/year. Total kilometer cover per trip is 42.7 km. HOMER depicts only ~1 ($0.012) taka per unit cost for harnessing energy from the hybrid microgrid system deployed in the Dhaka University campus with a feasible net present cost (NPC) of $676 (equivalent to BDT 54080). The variability of services can be developed and distributed in different ways because the same services could be offered with different frequencies during the days of the week or month. However, from this analysis, the system provides 23% of its energy generated for charging up the electric vehicles while the remaining 77% of the energy is sold back to the grid annually. It is remarkable for a country like Bangladesh to be able to provide extra energy to meet the daily demand.
It is also important to consider the environmental impact in terms of CO2 emission by the consumption of such conventional vehicles. The total emissions of CO2 from a conventional vehicle can be calculated as [25]: where CO2,CV is total emissions of CO2 from the conventional vehicle for each kilometer travelled; FC is fuel consumption expressed in g/km; CO , is the amount of CO2 produced from the combustion of a gram of gasoline. The complete combustion of 1 L of gasoline produces 2.4 kg of CO2. Assuming a density of 700 kg/m 3 , 1 g of gasoline produces 3.42 g of CO2 [25]. Finally, is a correction factor that takes into account the production and distribution of gasoline. Sullivan et al. (2004) suggests a correction factor of 1.162 for gasoline cars [24].
In conventional vehicles, which have on average 11.102 L/42.7 km of fuel consumption, the CO2 emission can be calculated around 1033.25 g/km/trip. In our case, per year the vehicle needs to cover around 51,240 km, which in turns gives per year CO2 emission of approximately 52,943.75 kg/year, this value has been calculated considering the route distance of 42.7 km per trip, which is currently being travelled using conventional gasoline engine busses whose approximate fuel consumption is around 11.102 L. We have considered 14 seated buses for our calculation. However, this value may vary depending on different road and driving conditions. Figure 8 shows yearly CO2 emissions for the oil-based transport system. Hence, we can clearly see that our proposed model can also save the environment by reducing CO2 emissions. From the foregoing discussion, the importance of green mobility at the urban level can be appreciated in a one-year period. Although producing clean energy is desirable, there are some drawbacks that are major concerns for future research work. The first limitation is that the two buses can only be charged up from the university campus. There are no other charging stations throughout the route. Therefore, if an unexpected mishap occurs and the bus cannot be charged up, then the transportation facility would have to be canceled for that day. Secondly, grid integration from the  From the foregoing discussion, the importance of green mobility at the urban level can be appreciated in a one-year period. Although producing clean energy is desirable, there are some drawbacks that are major concerns for future research work. The first limitation is that the two buses can only be charged up from the university campus. There are no other charging stations throughout the route. Therefore, if an unexpected mishap occurs and the bus cannot be charged up, then the transportation facility would have to be canceled for that day. Secondly, grid integration from the microgrid system is also a big challenge. If perchance there is difficulty to interconnect the system to the national grid, then the stored energy will be sold out, keeping a good profit margin [24].

Conclusions
In this paper, we have proposed a complete new use for the existing installed solar PV panels at the selected location, which will optimize the uses of the installed system. As the current system is only being used to supply energy to the grid, we have performed an analysis that proved that the efficiency of the generated energy can be enhanced by introducing an electric vehicle charging system. Our study has shown that the overall cost of energy will be reduced remarkably as the system is already built into the university campus so that the overall zero installation cost is needed to run the system. The energy produced by the solar photovoltaic system installed in the Institute of Energy of Dhaka University can provide up to 13,792 kWh/year, which can be utilized in a charging station (2861 kWh/year) for two electrical buses and can be imported or constructed from the local market. Approximately 21% of the total production can be used in the charging station for charging the electrical vehicles and the rest of the energy can contribute to the national grid (about 9837 kWh/year).
The maximization of the energy flow from the PV system to the electric vehicle requires quite long and low power charges that allow exploiting the hours when the production of the photovoltaic shelter is high. However, a good idea could be to use an energy storage system.
Moreover, using this new concept of green transportation will ultimately reduce the greenhouse gas emissions by 52,944 kg/year. Therefore, environmental pollution will reduce significantly. Overall, green transportation will be extremely beneficial for the economy of the country as it will reduce total load pressure on the electricity grid network and for the environment as it will lessen the CO 2 emissions in the air.