Application of Composite Method for Determining Fault Location on Electrical Power Distribution Lines

Distribution line is one of the most important components of the distribution system. Troubleshooting faults on these lines are often a tedious task requiring service vehicles and personnel moving from one place to another in order to locate the fault and fix the problem.'e study, therefore, is on how a composite fault location technique can be applied to predict the location of faults on the distribution lines. 'e calculations for the estimation of the fault location are performed using one terminal voltage and current data of the distribution line. A composite method that combines the impedance-based method and the fuzzy inference system method is used in the fault location algorithm. 'e presented algorithm has been extensively tested using the MATLABSimulink model of a 33KV 40-kilometer distribution line. 'e simulation result demonstrates good accuracy and robustness of the algorithm.


Introduction
In developing countries, inadequate provision of social amenities abound which undoubtedly include poor electricity supply. Distribution of electricity in these areas has been haunted by continuous malfunctions of electrical equipment especially distribution lines. So far, corrective maintenance is often done by the usual method; that is, personnel patrol around in a service van from place to place in an effort to locate the fault [1]. Responding to this situation in this manner is unarguably inefficient as the patrol team spends time locating the fault and, in some cases, may mistake the place where the fault occurred for another place.
is has led to lengthened downtime and hence has made power delivery unreliable. erefore, there is a need for a timely, effective, and efficient method of locating faults. is paper discusses a technique in the maintenance of electricity distribution infrastructure by bringing about on-time location of faults.
Maintenance is defined in [2] as the combination of all technical and administrative actions with the intention of retaining an equipment in (or restore it to) an operating state in order for it to perform its required functions. It is also defined as any work undertaken in order to keep or restore a facility to any acceptable standard. As stated in [2], there are two broad types of maintenance, namely, preventive maintenance and corrective maintenance. While preventive maintenance includes condition monitoring and servicing, as well as planned outages, corrective maintenance involves modifying faulted equipment so as to restore normal operation.
is paper addresses the problem of corrective maintenance on distribution lines.
According to [3], faults can be caused by short-circuits, faulty equipment, disoperation, overload, growing vegetation, aging, etc. Based on statistics, line faults happen to be the commonest faults in power systems [3]. Line faults that occur in power systems include single line-to-ground, lineto-line, double line-to-ground, and balanced three-phase faults [4]. Faults may be temporary (if the fault is cleared after the circuit breaker closes back) or permanent (if the fault is not cleared after opening and closing of the circuit breaker) [5]. Permanent faults can lead to loss of service lines and as such must be traced so as to restore operation [5]. Fast response times are also important to ensure continuity of service because the availability of power supply increases for shorter mean times to repair (MTTR) [6].

Literature Review
In all the methods studied in the course of this work, there is similarity in their overall design. ey all include a fault locating system and a means of communicating the location to the repairs people. Several works have been done in a bid to design an accurate fault locator. e various methods designed include impedance-based method, travelling wave method, noncontact magnetic field measurement method, fuzzy inference system method, and artificial neural networks method [3,6]. ese methods are by default used for transmission lines but can also be used for distribution lines [3][4][5][6][7][8][9]. If Global Positioning System (GPS) capability is added to the setup, the method is said to be synchronized, but if not, it is said to be unsynchronized [6]. e impedance method is the commonest one. It can be one-ended, twoended, or multiended [3]. It leverages on the assumption that the line is uniform; that is, the line parameters are distributed evenly throughout the line and therefore they can be obtained by ordinary methods for analyzing transmission line [3]. e prefault and postfault voltages and currents and their symmetrical components are obtained and, together with the line parameters, are used to estimate the fault location. It is for a fact that uneven spacing between the phase conductors causes line inductance to vary; temperature of the day affects line resistance and the amount of sag of conductors (due to thermal expansion) which in turn affects line capacitance [4]. is method has been revised in the "modified" impedance method [7]. By way of illustration, for simplicity, suppose that the algorithm gives a fault point, Y, for an input current, X, and the algorithm can be tested using example cases of known fault points. A pattern in the error may be discovered after which the algorithm is improved [7]. In the travelling wave method, either the disturbance created by the fault on the line is detected and analyzed or impulse voltages are injected into the line and the reflected wave is observed using time-domain reflectometry (TDR) in order to determine the impedance characteristics of the line [3,8]. Like the impedance method, it can be one-ended, double-ended, or multiended [3]. e wave captured usually contains noise that must be filtered out. A signal processing method using wavelet transform is employed to do this [9]. e noncontact magnetic field measurement method involves the use of a magnetometer (which contains a magnetic sensor) to sense the magnetic field produced by a fault current and relay the data so gotten to a central unit for processing [3]. e fuzzy inference system formulates mappings between fault currents and voltages (inputs) and the location of the fault (output). It does this using a series of fuzzy if-then rules. A merit of this method is that it follows human intuition and takes advantage of the fact that results are not always exact. A limitation of the fuzzy inference system is that it is only useful when its parameters are well tuned. e artificial neural network (ANN) method uses a network of nodes or objects whose output depends on the input(s) and an internal mechanism that can be modified on training. is gives the network the property of being able to learn. An artificial neural network, which is one of the soft computing techniques, requires a model to be trained with actual fault data. e data need to be up-to-date to take into account changes happening on the line with time and have to be unbiased so that the model will be accurate [9]. A demerit of the ANN method is that the accuracy of the model increases with increase in its complexity (i.e., depth of the network) and with the amount of data it is trained with [9]. Sometimes, more than one of these methods is employed in parallel, in which case they are called composite methods, in an effort to minimize the error that ensues [10,11].
A new and state-of-the-art method is the smart fault location method. is is a feature of major electric power systems of the world today [3]. is makes use of intelligent electronic devices (IEDs) installed throughout the power system to monitor it around-the-clock [5]. e IEDs act as sensors and relay sensor data, for example, temperature of component and line current, to a control station [12]. is has been made possible with advances in Big Data and radio silicon and wireless sensor network technologies [12]. ere is incentive to adopt this method because of the flexibility and scalability it affords, especially for smart power systems. An advantage of a smart power system is the economy in power supply it provides through efficient energy management systems and support for distributed generation to augment the conventional power generation [10]. It also makes static var control and "self-healing" in power system networks possible through coordinated transmission and distribution of electric power [10]. But the infrastructure to put this in place is expensive, although there has been progressive decrease in costs as a result of advancements in integrated circuit (IC) technologies, information and communications technologies (ICT), and battery production technologies [11]. As stated in [5], a smart fault location system will use knowledge of the network parameters, current topology, and type of data to determine the fault location method that best suits the situation.
ere are different software tools and associated hardware in use today with the fault location methods to monitor transmission and distribution systems and hence faults in them. Traditionally, remote terminal units collect measurements (bus voltages, currents flowing in the lines, frequency, breaker status, transformer tap position, etc.) called supervisory control and data acquisition (SCADA) from monitored equipment using field devices like sensors and measuring instruments [13]. Control action is carried out using on-site programmable logic controllers or remote terminal units [13]. is arrangement incorporates a software application that provides a graphical user interface for monitoring of the system [13].
In the work of [14], the identification methodology of main distribution line faults in OV MV BPL networks was presented and assessed. Result of the work shows that the identification of main distribution line faults is based on the coupling reflection coefficients derived from the original and the extended TM2 methods as well as their differences. Federico and Tonello in their paper [15] used two monitoring techniques, namely, the symbol level sensing and mains level sensing, which allow monitoring different types of anomalies. e results show that correctly identifying and locating an anomaly does not depend much on the size of the network or on the noise but rather on the topology of the network and how it is taken into account by the detection and localization algorithms.
In the methods described so far, impedance method is the cheapest and simplest method to implement. A combination of the impedance method with any of the artificial intelligent methods of fault location will give good precision of the fault location. In this paper, the impedance-based method and the fuzzy inference system are used.

Methodology
A composite method combining the impedance method and the fuzzy inference system method is used as the fault location algorithm.

Impedance-Based Method.
A single-ended impedancebased method is employed as measurements will be obtained at the substation. In the impedance-based method, first the symmetrical components of the fault currents are obtained by evaluating the analysis equation as follows: On the basis of the result, the fault type can be ascertained as different fault types have different effects on the line. In order to draw the equivalent sequence network, the sequence impedances of the sequence networks must be determined. To do this, the line impedances have to be transposed so that self-impedances of the line become equal and mutual impedances of the line become equal. en the sequence impedances are found by the following: For a transposed line, Z s and Z m are the self-impedances and mutual impedances of the line, respectively.
By using the technique of symmetrical components, the phase-impedance matrix is transformed into the sequenceimpedance matrix using the following equation: where [A] is the symmetrical components transformation matrix: Or Z 0 , Z 1 , and Z 2 are the zero, positive, and negative sequence impedances, respectively. Z 0 , Z 1 , and Z 2 are calculated as follows: Z T is the transformer impedance. Z L is a function of distance along the feeder to the fault point: where s � length of line, r L � line resistance, D eq � equivalent spacing � (D 12 D 23 D 31 ) 1/3 , D s � self GMD of conductor, and K 0 � Earth and ground wire condition. Use So we get Z L in pu as e fault impedance Z f is where R FLT is the arcing fault resistance in ohms. us, the fault currents are as follows: As can be observed, the sequence impedances are functions of the distance s from the substation to the fault point. Since the parameter of interest is "s" and all other Journal of Electrical and Computer Engineering parameters are known or can be calculated, "s" can be easily computed.
For 3-∅ fault, For line-to-line fault, For single-line-to-ground fault, e flow chart for the impedance method is shown in Figure 1.
e Simulink model of the distribution system used for the impedance-based method is as follows.
e algorithm for the impedance-based method is done in the embedded MATLAB function of Figure 2. In Figure 3, the faults are placed at an interval of 10 km on the line. At any time, only one of the three-phase fault blocks is switched on.

Fuzzy Inference System.
e structure of the fuzzy inference system is as shown in Figure 4. e output of the system is the weighted average of the inputs based on the fuzzy logic if-then rules. e "if" statements are the antecedent blocks, while the "then" statements are the consequent blocks. e type of fuzzy inference system is the Mamdani fuzzy inference system because it gives fuzzy outputs, an indication that the result is an approximation. MATLAB's fuzzy logic toolbox is used to model the fuzzy inference system (FIS) and Simulink is used to test the system using SimPowerSystems library and fuzzy logic controller block. Two fuzzy inference systems were created. e first fuzzy inference system determines whether the fault is single-line-to-ground, line-to-line, double-lineto-ground, or line-to-line-to-line, while the second fuzzy inference system determines the location of the fault. e ratios R 1 , R 2 , and R 3 are calculated first and normalized to get R 1n , R 2n , and R 3n of R 1 , R 2 , and R 3 , respectively, followed by the differences ∆ 1 , ∆ 2 , and ∆ 3 . is is as follows: (28) e ratios R 1 , R 2 , and R 3 determine the relative magnitude of the current in each phase with respect to another phase; it is expected that the phase (or phases) where the fault has occurred is the phase (or phases) with the largest current(s). Dividing the ratios by their maximum normalizes the ratios so that they have values between one and zero. ∆s determine the phases that are connected in a line-to-line fault; a small value for delta implies that the phases are connected in a line-to-line fault. If all three ∆s are small, a three-phase fault exists between the three phases. In the event that a fault to ground occurs, the neutral current is no more zero, which implies that the zero-sequence current is not zero.
e zero-sequence current is given as

Journal of Electrical and Computer Engineering
where I a , I b , and I c represent phase 'a,' phase 'b,' and phase 'c' currents, respectively, and I 0 and I N are zero-sequence and neutral currents, respectively. To take into account the zerosequence current, ∆ 4 is computed using the following equation: A large value for ∆ 4 shows the presence of a ground fault. e values of ∆ 1, ∆ 2 , ∆ 3 , and ∆ 4 show what type of fault occurred. ∆s calculated are not sufficient for fault classification; the phase differences between positive and negative sequence currents of each of the unbalanced current phasors have to be found. ese are represented by angle A for phase "a," angle B for phase "b," and angle C for phase "c." e angles can be determined bearing in mind that the negative sequence is the positive sequence reversed. For a single-lineto-ground fault, phase "a" currents of the sequence networks are in phase; therefore, where arg(I a1 ) and arg(I a2 ) are the arguments of the positive and negative sequence components of current in phase 'a'; arg(I b1 ) and arg(I b2 ) are the arguments of the positive and negative sequence components of current in phase 'b'; and arg(I c1 ) and arg(I c2 ) are the arguments of the positive and negative sequence components of current in phase 'c.' e absolute value sign clears any negative that may arise from taking the difference. For three-phase faults, arg(I a2 ), arg(I b2 ), and arg(I c2 ) have no significance, since the fault is a balanced fault. (c) Defuzzification. To defuzzify the output, the centroid method is used. e outputs are the fault types: single-lineto-ground, double-line-to-ground, line-to-line, and threephase faults.

Fault Location FIS.
is takes as inputs the fault type from the first FIS and the fault currents detected by the CTs. Given the fault type and values of fault current, it outputs a distance s that corresponds to the pair. In the simulation, the faults are placed at intervals of 10 km in a 40 km line. With the knowledge of the maximum fault current that can flow on the line (when the fault occurs very close to the substation) for a given fault type, the fault location FIS is able to predict the location of the fault by associating different fault positions to different faults types. e if-then rules are listed in Appendix B.
e Simulink model for the entire setup is shown in Figure 5.
e Simulink model for the distribution subsystem of Figure 5 is shown in Figure 6

Simulation and Results
In the MATLAB simulation, three-phase faults were placed at intervals of 10 km on a 40 km distribution line and the impedance-based method and fuzzy inference system method were used to estimate the location. e results of the simulation are shown in Figure 7.
As seen from the graph, taking the average is more accurate than using the result obtained from any of the two methods alone. If the error is estimated and added to the average fault distance, a better result will be obtained.

Application of the Proposed Method in the Underground Distribution System.
e proposed methods were applied to a 40 km underground distribution system. e simulation results are shown in Figure 8.

Conclusion
In this work, an algorithm for calculating distance to the fault location on the distribution lines using impedancebased method and fuzzy inference system method was developed and applied on three-phase overhead and underground distribution systems. e algorithm can be implemented using information from a microprocessorbased relay, a microcontroller, and a simple spreadsheet, making both methods accessible tools for the small utility. e fuzzy inference system method should provide improvement over the impedance-based method for faults when the parameters are well tuned. Although the   simulation result shows that the composite technique is of good quality, the error in fault location estimation can be limited by calculating the error factor and multiplying the average fault distance by the error factor. is will give an improved average fault distance, thereby forming a good basis for small utilities to develop their own fault location method.